I have built a small building on the back of my land that I plan on wiring myself. The electric co-op set a pole and meter about forty feet away, and I plan on going underground service to my panel in the building. Main disconnect on pole under meter. A friend tells me under 2008 code I must run four-wire cable entrance instead of three. Is this correct?
Even if you are not under the 2008 NEC yet, it is best to run four wires from the disconnect to the subpanel in the outbuilding. That would be two hots, a neutral, and a ground. You will need to isolate the neutral bar from the panel enclosure and add a ground bar that is bonded to the enclosure. You will also need to install ground rods at the meter pole AND at the outbuilding.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 21 Ways to Spring Clean—Naturally
- Show Off: 9 Ways to Display a Collection
- The Best Paint Colors for Low-Light Rooms
- 7 Easy Budget-Friendly Backyard Makeovers
- 8 Clever Storage Solutions for Pots & Pans
- 8 Creative OTHER Ways to Use a Closet
- 12 Tiny Gardens to Grow on a Tabletop
- 15 Eye-Catching Front Door Options
- 12 Places You Never Clean—But Should!