I have built a small building on the back of my land that I plan on wiring myself. The electric co-op set a pole and meter about forty feet away, and I plan on going underground service to my panel in the building. Main disconnect on pole under meter. A friend tells me under 2008 code I must run four-wire cable entrance instead of three. Is this correct?
Even if you are not under the 2008 NEC yet, it is best to run four wires from the disconnect to the subpanel in the outbuilding. That would be two hots, a neutral, and a ground. You will need to isolate the neutral bar from the panel enclosure and add a ground bar that is bonded to the enclosure. You will also need to install ground rods at the meter pole AND at the outbuilding.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- Make Your Bed: 9 DIY Headboards
- Insanely Easy 60-Minute Home Improvements
- Space-Saving Solutions for Tiny Bedrooms
- 9 Perfect Color Combos for Your Home
- 22 Tiny Houses We Love
- See the Most Highly Anticipated Colors for 2015
- What's the Best Color for Living Rooms?
- Favorite Space-Saving Double-Duty Furniture
- 10 Low-Cost DIY Home Security Solutions
- Redecorate Without Spending a Dime: 10 Ideas
- 10 Houseplants You Can Grow Anywhere
- 9 Amazing Mobile Home Makeovers
- 10 Doable Designs for a DIY Rug
- 9 Alternative Uses for Toothpaste
- Live Large in a (Very) Small Space
- 8 Cheap and Unique DIY Nightstands
- 15 Eye-Catching Options for Your Front Door
- Supersize Your Small Bath with 8 Pro Tips
- Don't Try This at Home: 7 Dangerous DIYs
- 10 Simple Woodworking Projects
- Is There Anything Vinegar Can't Do?
- 7 Incredible Uses for Salvaged Lumber
- 12 Tiny Gardens You Can Grow on a Tabletop
- 16 Sneaky Storage Ideas
- 10 Surprisingly Smart Solutions for Junk Drawers
- Bright & Bold Colors for Your Front Door
- DIY Bookcases: 16 Easy Project Ideas
- Don't Make These 7 Fireplace Mistakes