i hooked this up once before but now it doesnt work.
i have a black and white wire that i have running up form the basement out of a junction box. i have it connected to the recept side of the togle switch-outlet (black on copper white on nickle plate screw.) then i have a black and white wire running up the wall to the light i put in. ive tested the power to that wire wire and its telling me i have power to that light but it wont turn on. and yes the light fixture does work and so does the light bulb. i checked them both just minutes ago to be sure. i bought a new switch and outlet and there is a breakoff tab it says that im suppose to remove. can u tell what that is? not sure if its the small white plastic piece or if its the copper tab. thanks
the only reason you would need to remove the tab would be if you wanted to control the outlet on "that" device with the switch.
i want the switch to just control the light and have the outlet live all the time. so inorder to do that the tab must stay on? ok then why does the outlet work but the light wont turn on?
- 15 Old House Features We Shouldn't Abandon
- 13 Lazy Cleaning Tricks for a Spotless Home
- Laundry Room Ideas to Knock Your Socks Off
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 7 House Sounds You Never Want to Ignore
- 10 Surprisingly Simple Woodworking Projects
- Worth It: 8 Renovations That Pay You Back
- Organize Your Life with 12 Dollar-Store Buys
- 9 Totally Amazing Mobile Home Makeovers
- Don't Make These 7 Mistakes in Small Spaces
- 20 Sneaky Storage Ideas
- 15 Totally Unexpected DIY Flooring Alternatives
- 7 Easy Budget-Friendly Backyard Makeovers
- 10 Closet Cures That Cost Less Than $100
- 11 Easy DIY Projects to Declutter Your Home
- 10 "Zero Dollar" Garden Hacks
- 10 Killproof Plants for a No-Effort Landscape
- 9 Insanely Easy 1-Hour Backyard Projects