Adding a zone valve is the only way to take control of the heat on the 2nd floor. Additional t-stat also needed to control this valve.HOLLYWOOD.
Possible causes for increased pressure. - water fill valve leaking by. - Expansion tank water logged/too small - Water temp too high. set betwee...
Answer: Aprox. ONLY Length x Width X 45BUT's per sq. ft. Ex: 1600sq' x 45 = 72,000 BTU/hr Proper heat loss calculations is always the way...
The answer to your Q: is Yes. A Heating proffesional should look at the system. I cannot tell if you have Hot Water or Steam Heat, Room size is i...