# Retrofit?

If this is on an existing flat wall, use the Arlington 8161 siding block. http://www.aifittings.com/k_6.htm

If this is on an existing flat wall, use the Arlington 8161 siding block. http://www.aifittings.com/k_6.htm

over 7 years by **househelper**

1

answers161

ViewsCheck for power at the box, double check the wiring, make sure any switches are on, check the DIP switches on the remote and receiver to make sure ...

over 7 years by **househelper**

1

answers699

ViewsHow are the red and black wires connected at the breakers? They need to be on breakers that are mounted one above the other so that each is on a di...

over 7 years by **househelper**

13

answers530

ViewsIf you are looking at using an electric on demand, make sure you have sufficient capacity to support it. The electric units require a 70-80 amp sup...

over 7 years by **househelper**

1

answers715

ViewsYou can still find the plastic GE load centers, but you are looking at only 4-6 circuits. Check your local hardware store.

over 7 years by **househelper**

2

answers757

ViewsThe oil will retain heat longer due to its higher viscosity, but as Bill points out, it will cost the same to heat either.

over 7 years by **househelper**

4

answers628

ViewsAt the first GFCI receptacle you will have 12/3 in, 12/2 out to the next GFCI (other circuit) and 12/2 out to the first protected receptacle on cir...

over 7 years by **househelper**

3

answers920

ViewsDo the instructions say it requires a 30A circuit or that it draws 30A? Big difference. If a 30A circuit is required, then 10/3 with ground and a 3...

over 7 years by **househelper**

5

answers73

ViewsThe NEC does not require you to secure NM wiring when fishing inside finished walls.

almost 8 years by **househelper**

4

answers798

Views"the voltage on one leg can exceed 250 volts while the other leg can fall to almost zero." For a loose neutral connection, that is not true. The...

almost 8 years by **househelper**

7

answers218

Viewsand because it is a trailer, you will need 4 wires (H, H, N, G). There are direct burial quadriplex cables available for use as a mobile home feede...

almost 8 years by **househelper**

3

answers515

ViewsCorrectly called an open neutral. Biggest offenders are squirrels. They like to chew on the uninsulated aluminum. Many jurisdictions are going to c...

almost 8 years by **househelper**

7

answers118

ViewsAt the ceiling fan you should connect the white to white, black to black, and blue to red. At the switch, for the cable from the ceiling, connec...

almost 8 years by **househelper**

2

answers940

ViewsSince this is in a basement, you may have a GFCI receptacle (rectangular receptacle with "test" and "reset" buttons) protecting a portion of that c...

almost 8 years by **househelper**

4

answers180

ViewsSince you are routing the feeder through the attic, you will need to use #2 Cu or 1/0 Al according to Table 310-15 (b)(6).

almost 8 years by **househelper**

3

answers707

ViewsDoes your panel have a main breaker that can be shutoff? If so, does the fan/light go off then? If not, try turning all the breakers off at the sam...

almost 8 years by **househelper**

5

answers518

ViewsYou certainly have a right to question the charges and ask for clarification. Are these labor only charges? Is the hourly rate typical for your are...

almost 8 years by **househelper**

2

answers663

ViewsTry incoming white to PES and light white, black to PES black, PES red to light black.

almost 8 years by **househelper**

2

answers798

ViewsYou may also have a GFCI receptacle that has tripped. Look in bathrooms, garage, kitchen, outside.

almost 8 years by **househelper**

2

answers240

ViewsMake sure you are turning the breaker completely off before trying to reset. If it continues to trip, your electrician will disconnect the wire fro...

almost 8 years by **househelper**

2

answers445

Views