SImply instll the blower door and turn the unit into a call for heat, set to heat and turn the desired temp up as high as it goes. The induced dra...
JGRIZZMember since 12/16/04
Does it have a hot surface ignitor or spark ignition? There should be a self test diagnostic on the unit. Also my guess is that if the gas flows bu...
The newer furnaces use a flame sensor to detect that the fire has indeed lit once the gas begins to flow, if no flame is sensed the control will sh...
I install every brand out there and in 20 years have had only three bad compressors. So-in my opinion every brand out there is just as good as anyo...
I do residential replacements all the time, but I operate differently than most comapnies. The thing you should know is that most of the equipment ...
Does your furnace have a spark ignition system, that makes a ticking sound at start up before the blower comes on? If so the clicking may be the fl...
PAckaged-split- Natural Gas-Propane all Electric Oil Fired. Digital thermostat or bymetal-mechanical? What are the colors of the wires on th...
So what is the efficiency of that furnace anyway? What is the model number and the Brand?
The motor sounds like a combustion blower motor, if it is in the flue exhaust system that is exactly what it is. If it is humming the motor is prob...
The main wires the black and the white may be reversed, the polarity may be reversed to the board. Simply switch the wires or reverse the plug.
The fan runs continuously because the 24 volt circuit is broken somewhere, and the relay on the board needs 24 volts to open the fan circuit to the...
sounds to me like the brown plate on the cabinet wall you describe is the high limit switch, this as an automatically resetting internal temperatur...