Pour the oil out. Pour a small amout of gasoline in and swish it around. Pour this out. Repeat this until all the oil appears to be out. once or t...
Are there more cables than you described in the boxes? Do you remember how it was connected before? Can you post that? Can you open the switch boxe...
Why do I have log in evrytime I come to the site since the new upgrade? I have cleared my cookies and files and I still need login everytime.
Keep looking for the GFCI. I have heard of them being in very weird places sometimes. I heard of one being in the attic once. That was a really dum...
Is it possible to run a line from perpendicular to the beam at the same height as the low side. Put a large ring in the suspension line at the same...
3way and 4 way switches are not all constructed the same. You need to determine the common screws on new switches. They will be black colored or ma...
Sounds like you may have tripped a GFCI. It is the receptacles with the TEST and REST button on it. The circuits you mention are all supposed to be...
If you have something plugged into another receptacle on the same circuit it will put current though the neutral wire of an unused receptacle. You ...
You need to open up some boxes and find the other end of the unused neutrals. How do you know they are not used? Then have some tug on them and fin...
If the power comes into the switch you could replace the switch with a switch receptacle combo.
Give us a complete list of all the cables in each box(both switches and the light fixture) and where the wires from each cable go. Ignore the groun...
Take a close look at the old receptacle. I think you will find the tab is broken off the hot side. The tab only breaks off the hot side not the bot...
You have an open ground wire somewhere on the circuit. It could even be in the main panel. Is the entire circuit wired with 2 wire + ground cable? ...
Why don't you call some structural engineers and have them take a look. For a couple of 100 dollars you can get a real answer. If he finds real pro...
It sounds like the switch is operating properly. The pressure tank has lost its air charge. Turn of the pump and turn on a tapuntil the pressure in...
There should be a small hole beside the one that the wires are pushed into. Insert a small wire into that hole and it should release the wire. If i...
If you can't get below frost line, you could use a system like this. It is a heat cable that goes inside your water line. http://www.deanbennett...
I am going to guess that you have an electric heater somewhere that is not turned off. On a cold day go to your breaker box and start turning off b...
Your house does not have ground wires. You can not replace the receptacles with 3 prongs grounded. You can replace them with GFCI receptacles and u...
You applied the varnish too thick. All you can do is wait for it to harden the sand smooth and try again. Since the varnish is on thick it will tak...