If the new slab is at least 4 inches you won't have a concrete problem. You will have a garage door problem as you will now need a special sized do...
You connected the wrong wire to the common on the new dimmer. You have 2 more chances to get it right.
Is the dryer out also? If it is and your main is not tripped I think you call the power company and have them check your incoming power. One side o...
I thought of something that might be easier.Remove one of the connection and use a siphon hose. Then pour some RV/Plumbing anti freeze in.
You could try alcohol. It might disolve the glue. If that doesn't work look for a product called goo gone.
You need to drain it. Disconnect the inlet and the outlet pipes and tip it up to drain the water. Otherwise provide a heat source to keep it from f...
I once saw a guy score it with a good heavy knife and then flex it. It snapped off clean. This was for straight cuts.
It could be a dip tube problem. It gets worse in the winter because the water entering the water heater is colder.
If there are only 2 wires/1 cable at the light when the switch is off NO voltage should be present on any wires. If you are using a high impedance ...
You can start at one end of any wire you don't use any more and just start pulling it out. When you get to a joint/splice disconnect it. There is n...
IT sounds like the opener is jammed. There are many plastic gears in these units. One could be broken. The chain could be jammed or off the pulley.
My list of soluions.1. Check humidity level. Should be around 35%. Use the bathroom ventilation fan when takeing showers etc.2.Remove any air defle...
You could connect the shower light to the existing bathroom light. You don't have to go to the switch box unless that is the prefered location. At ...
It sounds like the neutral wire is being switched. Can you tell me what are the connections in the switch box? There should only be black wires on ...
You have been given the wire sizes for the 15 and 20 breakers. The recepticles even though marked 15 amp can be used on a 20 amp circuit.
He can't red tag you because he doesn't like the electric company complaining to him. He has to site a code reference. Ask him for the specific cod...
If this is a switch loop the white should hot going to the switch and black switched hot coming back from the switch to the light.How many cables a...
If you only removed the 3 wires on the dimmer then you connected them wrong to the new dimmer. Read the directions and determine which wire of the ...