For maximum sound deadening use resiliant bars. They are Z shaped and screw to the joist and then the panels screw to them.
You should try and find the electrician first. Many of them will not likely take on ahlf the task as you are planning. It would be a pain to get th...
You have two fixtures and two transformers. You would be better off to put one transformer for each fixture.
What is your location? In Canada it is legal to run a ground wire to the copper pipe if the pipe is properly grounded/bonded. I don't think I woul...
You can not put duplex receptacles on a 30 amp circuit. You must change that breaker to match the wire size. 15amp for #14, 20 amp for #12. This...
You can not put duplex receptacles on a 30 amp circuit. You must change that breaker to match the wire size. 15amp for #14, 20 amp for #20. You co...
Yes. It is OK to use larger wire than the code requires. Some times it is even necessary for long runs to avoid voltage drop. It is however not g...
You need to install a junction box at the new location of both your lights. If you are lucky the wires are long enough and the exisitng box can be...
Empty receptacles don't use any power. It all depends on what you plug in them. If you plug in a heater then one receptacle is enough. The flicker...
You don't normally do it that because you need 4 wire+grd cable between the lights. If you let = represent 3 wire and- represent 2 wire you should...
I don't think wireless will for this. The receiver actually puts voltage to the dish though the cable.
If all the lights are between the switches you need a 4 conductor cable to make them work. You probably only ran three conductor and they are wired...
You can do it if you use a GFCI combo device. It is legal to use a GFCI to replace an ungrounded receptacle witha three prong receptacle.
If the hot spot is on a slab then you could have abusted hot water line under the floor. Chaeck your water meter with everything turned off. It sho...
Sounds like an open neutral to me. Can you fix it? I don't know how smart you are. If every receptacle on the circuit is dead then the problem co...
The 16Kw is likely if all burners are on at the same time. Does it pop the breaeker with only one burner or are you trying to run every burner and ...
The heat from your new fixture will dry out the insulation of the old wiring. It will eventually crack and fall off creating a hazard of the wires ...
Your old wiring most likely doen't have a ground wire. That would be the fault.