could be flapper also not making a good seal.
Get Help from Bob Vila
- Give-Aways & Offers
- Monthly Must Do's
- DIY Project Ideas
- Step-by-Step Guides
- Inspirational Photo Galleries
i can't see any reason why a wall switch would be needed other than for convenience. the first one may have fried because you wired it for a load ...
you didn't say if it was new.and if you connected everything properly then just take it back.
"I bought the house and everything was new in the house" there you go.somebody "flipped"the house and goofed up the wiring.
what might help is fluidmaster makes a clorinating device that attaches to the refill tube and clorinates the water that goes into the bowl only.
pull the compressor disconnect and fire up the air.then turn on the radio. that would tell you if the compressor is actually generating the noise ...
the actual furnace,(not including the compressor)blower,relays,transformer,operate off 110.try plugging the radio into an outlet that is on the oth...
powering the radio off the other leg that the furnace is on for starters, then post back with results. is this something that always was or jus...
try closing off fixtures at the shutoff valves one at a time,thencall for water at another fixture and see if by isolating any one of them you can ...
but it all depends on what you have up there now meaning is there a joist right there or is the box centered between two. also it depends on the t...
sure is ok as long as it's flushing properly. you know how to adjust the level if you need to right?
i used to have the same problem until i started putting washer sets,brass and rubber,on both sides of the tank,then a nut,snug everything down,then...
you gave the model number of the mower not the part number. usually i can work with this but in this case the sears parts database is giving an er...
are those some kind of giant braided connectors between the pumps and the pipes to absorb vibrations? gotta be for a high rise. is one for back u...
checking the screens on the faucets.they're called aerators.they could be plugged. and that valve too.
usually you would be better off trying to get to the root of the problem instead of covering up or compensating for it.anyway here's a link.do you ...