if you can get the parts.i never did.i just replace them.couple dollars.
well it all depends.is it a dedicated line.what size is the wire.what condition is it in.what size is the fuse.what size is the air conditioner.as ...
i am inclined to believe that this is an issue with the breaker just not reseting and not an actual tripping situation. one way to verify this wou...
whatever it is it isn't in that box you were working on. see if you can find the main shutoff. another thing before calling electrician would...
you want to disconnect the wire from that breaker just to verify that you have a short. throw the main,disconnect the wire,turn the main back on,t...
start from scratch.take the switches out. leave the wires disconnected.then engage the breaker.see if it stays untripped.if it does then turn it of...
could be that you had a short before that you didn't know about. try disconnecting the new pigtail grounds (temporarily)and see if it stops trip...
that's the only way they can stay in business. i'm the only one who works for peanuts these days. now i'm laughing out loud. glad you got tha...
because if it doesn't work then you run the risk of it splashing in your face if you have to end up snaking the drain of have to take the trap off.
yes you need to get the water out before you start working on it.if that section is part of a loop then you have to tie those two together with a p...
plunger? hand held snake? or first try blocking off the no disposal side and filling the disposal side with water then turn on the disposal while y...
does it even have an aerator? the only place it could be is on the tip of the spout.you might end up taking everything apart again to see what is b...