I think it will be OK then. I'm glad you reinforced it. The longer you can wait the better. Cheers.
"Do blisters compromise the integrity of the slab?" Yes because the blisters are telling me you made the cement too soupy. Didn't you reinforce i...
Usually what I do is replace everything in the tank. Since you have to remove it anyway to replace the flush valve. Bolts,fillvalve,flush valve,tan...
Either way if it's set to the cooling mode cool air should be flowing if air conditioning is installed and working properly.
I've used rope before around the scaffold out one window and into another.Just for security. Just make sure you level it out from the start.
Usually you would want to go with a skylight (roof windows) in this type of situation due to the fact that when winter rolls around you want to clo...
Doesn't the thermostat get it's power from batteries? If so it should display a reading even it it isn't connected. What is the model # of the new ...
Suggestions: 1 use an easy out,2 just drill it out,3 If you have a dremmel you can cut a straight slot into it then use a screwdriver. That's abou...
Was the system working correctly before you changed the thermostat. If not what was it doing or not doing.
Sounds like a spring or a cable broke.I suggest you don't monkey with it and get a pro for this one.
Connect it back up the way you had it to begin with(brown to blue). It should work. There's no reason why it shouldn't after you set the pull chain...
Wait till it wears off then either recaulk with correct caulk or prime with correct(oil base)primer.
Unless there are gouges in the wood from the pressure washer then there is no damage. It just needs to be resealed with a good quality sealer. Afte...
Without seeing it happening it's impossible to say exactly where the problem is, but it is a serious issue that needs to be addressed. There must b...
Somtimes they can be pulled with a suction cup and somtimes they can be filled and painted like a car door.
It makes you wonder what other surprizes there are that the inspector can't see. Nothing was said until he took that cover off right? Anyway bottom...
Could be: Wrong contactor for application,poor connection causing overheating,poor coil voltage causing it not pull in tightly,too frequent compres...