sounds like the top 30 is mated with the first 50, and the bottom 30 is mated with the second 50. as far as i know, you cant buy this configuration...
old_timerMember since 07/30/02
are you saying that the former tenants ran all that equipment from the house service panel?....if so, then i imagine there was/is some definite "li...
are the breakers installed all on the same side of the 100 amp. panel?..if so, the problem may be an unbalanced load in the panel. and, yes, it pr...
for direct burial applications involving a 20 amp. circuit, use a 12/2 with ground "uf" type, buried 24' deep, and protected by a 20 amp. breaker
as an electrical contractor with 38 years in the trade, i have seen quite a bit of bad wiring, device mis-applications, and downright dangerous sho...