SafetyAlertsApril 24, 2003Panasonic Consumer Electronics Has Recalled cordless power tool battery packsSecaucus, N.J. (SafetyAlerts) - Panasonic C...
RmiellMember since 08/31/02
An easy way would be to nail the box onto a short piece of 2x4, then screw this to the metal stud.There are some brands of boxes that have screws i...
Alot of information will go into this determination. Follow this link to a standard table for different items included in the calculation. From t...
There are numerous rules about doing this work. I would suggest you contact a qualified electrician to do the work. Electrical safety should be f...
A phone call to the manufacturer will settle this issue. Make sure to get their opinion in writeing.Don't just call the seller, who will probably ...
You need to verify that the hot wires are installed correctly onto the line terminals of the gfci. Use a voltmeter to verify this. If the 2nd out...
If your "sub-panel" will be in an attached garage, then to ground it with an 8' ground rod would be a violation of the electrical code. If this is...
Two points, both which would lead me to believe you need to get an electrician in to "clean up" your electrical equipment.The first, you state that...
I agree with those that state there is no set way. To say one way is "proper" is misleading. There has been many pages written about this issue. ...