Are you saying that there is room for the box to go next to the existing one, but just nothing to mount it to?
txsparkyMember since 08/30/02
First look at you panel to see if it will accept the 1/2" breakers. The label should(may) have a designation such as 20/40 which simply means 20 1"...
You could mount a j-box next to the recessed can in such a manner that it would still be accessible by removing the can.
Bob jr, The voltage is 12. Thus 180w / 12v = 15 amps. This would be the total load on the x-fmer and the wire at the beginning of the run. Unless a...