- Give-Aways & Offers
- Monthly Must Do's
- DIY Project Ideas
- Step-by-Step Guides
- Inspirational Photo Galleries
Also, there is a good chance that the existing cables might not have an equipment ground. This was a common, code permitted practice in years gone by. It is no longer permitted.
I suggest installing a new 6-3 with ground cable, a new 50 amp breaker and a 50 amp 4 wire receptacle.