I just ran a new outlet to a bathroom yesterday. It's a single outlet on a GFCI circuit-breaker. It's the only thing on that breaker. Two years ago an electrician put in a kitchen outlet for me, which is also a single outlet on a single breaker (oddly, he didn't use GFCI).
It just now occurred to me that I could save a slot in my breaker box if I hung both these outlets off that new GFCI breaker that I put in yesterday. Plus, I'd get ground-faulting in the kitchen. The way the wiring's been done, this would be a trivial change to make. Does the NEC allow a 20-amp GFCI breaker to serve one outlet in a bathroom and one other outlet in a kitchen?
Get Help from Bob Vila
- Give-Aways & Offers
- Monthly Must Do's
- DIY Project Ideas
- Step-by-Step Guides
- Inspirational Photo Galleries