I am trying to figure out if the system ground that ties into the main service ground has to be an unspliced connection to all electrodes. Meaning, the 2 ground rods I have driven into the ground and the water pipe. I'd prefer to run ground wires from the main service to the ground rods and a seperate wire from the main service to the water pipe. Anyone know if this is OK?
Also, does the customer side of my gas meter pipe have to be bonded to ground. If so, does it also require an unspliced connection.
Get Help from Bob Vila
- Give-Aways & Offers
- Monthly Must Do's
- DIY Project Ideas
- Step-by-Step Guides
- Inspirational Photo Galleries