one question here.
installing a 100 amp lug subpanel in my basement to be feed from 100 amp breaker in main panel...
what type/size of wire am i asking for ?
You may use #4 copper (two hot, one neutral) and a #8 copper ground (insulated), type THHN or THWN in most jurisdictions.
If your work will be subject to inspection, many jurisdictions rigorously enforce the ampacity tables and the exception that allows #4 copper for dwelling services or "the main feeder" would not be allowed for a sub-panel. #3 THHN copper would be the minimum size and if you will be using a cable such as NM-B, #2 copper would be the required size. If in doubt, consult your local inspector.
100 amp lub subpanel from 200 amp main service panel
Dupont Real touch Elite Lamanite Flooring
remove wood filler from raw wood boards
- 7 Types of Homeowners Who Can Benefit from a Backyard Shed
- 50 Products for Quick Fixes Around the House
- How To: Keep Cool When You're Working Outside
- 21 Money-Saving Tricks Every Homeowner Needs to Know
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 7 House Sounds You Never Want to Ignore
- 10 Surprisingly Simple Woodworking Projects
- Worth It: 8 Renovations That Pay You Back
- Organize Your Life with 12 Dollar-Store Buys
- 9 Totally Amazing Mobile Home Makeovers
- Don't Make These 7 Mistakes in Small Spaces
- 20 Sneaky Storage Ideas
- 15 Totally Unexpected DIY Flooring Alternatives
- 7 Easy Budget-Friendly Backyard Makeovers
- 10 Closet Cures That Cost Less Than $100
- 11 Easy DIY Projects to Declutter Your Home
- 19 "Zero Dollar" Garden Hacks
- 10 Killproof Plants for a No-Effort Landscape
- 9 Insanely Easy 1-Hour Backyard Projects