I've installed a gfci breaker on my panel and connected an exterior light to it. When I turn the switch on it trips the breaker. When I disconnect the light from the wires and turn on the switch, nothing happens. With the light disconnected, the test button works as it should. I connected a different light and it still trips the breaker.
I'm wondering what I did wrong.
Get Help from Bob Vila
- Give-Aways & Offers
- Monthly Must Do's
- DIY Project Ideas
- Step-by-Step Guides
- Inspirational Photo Galleries