I would like a professionals opinion on a quality gas burner. Price not an issue
- Give-Aways & Offers
- Monthly Must Do's
- DIY Project Ideas
- Step-by-Step Guides
- Inspirational Photo Galleries
The plastic ones will melt just as fast as any other plastic of it's kind, they are constructed a little larger to accommodate better wiring method...
Call a qualified electrician ...."Electricity is not a hobby"When dealing with the breaker panel special care must be taken, there are live parts i...
You can install low voltage and line voltage together you will need a mechanical divider.But I don't recommend your Cat#5 data cable being so clos...
"Electricity is not a hobby"You probably have a problem with your neutral buss, but you should really have a qualified electrician look at this.
If I were you I would replace the box in the wall with a deeper on and run a dedicated circuit to the refrigerator and put in a single receptacle, ...
"Is it due to possible overheating"Absolutely ... the size of the conductors does dictate which box to use do to overheating.Also electricity does ...
If your going to do it, do it right.....Broan and Nutone are the best names out there, it's just about all that I put in
Are there any disadvantages in doing this? None whats so ever ...... I do that all the time when I'm working on a job with either a lazy "rocker" o...
Splice the red and the black together, this will make your receptacle "constant hot."Then you splice a little piece of wire to the red and black so...
If you haven't already have this solved just find the two wires that go to the light fixture and connect the new wires of your receptacle to the wi...
Dear Davey B:With electricity assuming something could get someone killed.Please be more explicit. What room is it in, is it a switch or receptacle...
if your house wasn't built after 1985 it's a good bet that you don't have wire rated for 90¬∫ .....
Dear Shuanm:Here is the article in the 1999 National Electrical Code Book (the latest edition)(personal observation: the indivual contuctor of 90¬∫...
Dear Steve:If you had an email address I would have sent you a few articles from the 1999 National Electrical Code Book (latest version available. ...
Dear jhami:The application you described sounds like what some of us in the trade call a "feed through", the black and the white wires were already...
Dear Steve:Here are some codes from the ‚Äú1999 National Electrical Code Book‚Äù(1)Spacing. Receptacles shall be installed so that no point along t...
George can you be more explicit in your description of a "Pigtail"?There are some of us in different parts of the States that use different slang t...