You didn't say what kind of plumbing you've installed. If it's plastic, there's no point in placing a ground on it.
Is there a grounding rod outside?
[This message has been edited by rpxlpx (edited December 03, 2002).]
Yes, I have a grounding wire that is going outside. I am putting either PVC or copper plumbing back in.
Any copper plumbing you install should be bonded back to the bonded buss bar in the service or building disconnecting means. In order to serve as a grounding electrode for your home the clamp should be attached to an underground metal water pipe within five feet of were it enters your home. There must not be any plastic pipe or insulating fittings between the point of attachment and the underground piping. The best practice is to make the grounding connection on the supply side of the first control valve in the water line. Since no one is going to cut in to a pipe they can't shut off that prevents later plumbing work from leaving the home ungrounded.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 21 Ways to Spring Clean—Naturally
- Show Off: 9 Ways to Display a Collection
- The Best Paint Colors for Low-Light Rooms
- 7 Easy Budget-Friendly Backyard Makeovers
- 8 Clever Storage Solutions for Pots & Pans
- 8 Creative OTHER Ways to Use a Closet
- 12 Tiny Gardens to Grow on a Tabletop
- 15 Eye-Catching Front Door Options
- 12 Places You Never Clean—But Should!