You didn't say what kind of plumbing you've installed. If it's plastic, there's no point in placing a ground on it.
Is there a grounding rod outside?
[This message has been edited by rpxlpx (edited December 03, 2002).]
Yes, I have a grounding wire that is going outside. I am putting either PVC or copper plumbing back in.
Any copper plumbing you install should be bonded back to the bonded buss bar in the service or building disconnecting means. In order to serve as a grounding electrode for your home the clamp should be attached to an underground metal water pipe within five feet of were it enters your home. There must not be any plastic pipe or insulating fittings between the point of attachment and the underground piping. The best practice is to make the grounding connection on the supply side of the first control valve in the water line. Since no one is going to cut in to a pipe they can't shut off that prevents later plumbing work from leaving the home ungrounded.
- 15 Old House Features We Shouldn't Abandon
- 13 Lazy Cleaning Tricks for a Spotless Home
- Laundry Room Ideas to Knock Your Socks Off
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 7 House Sounds You Never Want to Ignore
- 10 Surprisingly Simple Woodworking Projects
- Worth It: 8 Renovations That Pay You Back
- Organize Your Life with 12 Dollar-Store Buys
- 9 Totally Amazing Mobile Home Makeovers
- Don't Make These 7 Mistakes in Small Spaces
- 16 Sneaky Storage Ideas
- 15 Totally Unexpected DIY Flooring Alternatives
- 7 Easy Budget-Friendly Backyard Makeovers
- 10 Closet Cures That Cost Less Than $100
- 11 Easy DIY Projects to Declutter Your Home
- 10 "Zero Dollar" Garden Hacks
- 10 Killproof Plants for a No-Effort Landscape
- 9 Insanely Easy 1-Hour Backyard Projects