You didn't say what kind of plumbing you've installed. If it's plastic, there's no point in placing a ground on it.
Is there a grounding rod outside?
[This message has been edited by rpxlpx (edited December 03, 2002).]
Yes, I have a grounding wire that is going outside. I am putting either PVC or copper plumbing back in.
Any copper plumbing you install should be bonded back to the bonded buss bar in the service or building disconnecting means. In order to serve as a grounding electrode for your home the clamp should be attached to an underground metal water pipe within five feet of were it enters your home. There must not be any plastic pipe or insulating fittings between the point of attachment and the underground piping. The best practice is to make the grounding connection on the supply side of the first control valve in the water line. Since no one is going to cut in to a pipe they can't shut off that prevents later plumbing work from leaving the home ungrounded.
- 15 Old House Features We Were Wrong to Abandon
- 17 Tiny Bathrooms We Love
- 20 Insanely Easy 60-Minute Home Improvements
- 17 Design Inspirations for Mudrooms and Entryways
- 25 Clever Ideas for Repurposed Storage
- 10 Clever Uses for the Space Under the Stairs
- Laundry Room Ideas to Knock Your Socks Off
- 30 Things Every Homeowner Should Know How to Do
- 11 Clever Alternatives to Kitchen Cabinets
- House Quiz: Test Your Knowledge of U.S. Architecture
- 10 Things You Can Build with Plumbing Pipes
- Sweet Dreams: 16 Inventive Beds You Can Make Yourself
- Kitchen Envy: 10 Rooms We Love
- 16 Ingenious IKEA Hacks
- 18 Clever and Easy DIY Ways to Use Rope at Home
- 10 Eye-Catching Options for Your Front Door
- 10 Room Dividers to Bring Order to Your Space
- 9 No-Sew Fabric DIY Projects to Dress Up Any Room
- Tips and Tricks to Fit More into Less Closet Space
- Secret Rooms: 10 Special Spaces Hidden from Sight