You didn't say what kind of plumbing you've installed. If it's plastic, there's no point in placing a ground on it.
Is there a grounding rod outside?
[This message has been edited by rpxlpx (edited December 03, 2002).]
Yes, I have a grounding wire that is going outside. I am putting either PVC or copper plumbing back in.
Any copper plumbing you install should be bonded back to the bonded buss bar in the service or building disconnecting means. In order to serve as a grounding electrode for your home the clamp should be attached to an underground metal water pipe within five feet of were it enters your home. There must not be any plastic pipe or insulating fittings between the point of attachment and the underground piping. The best practice is to make the grounding connection on the supply side of the first control valve in the water line. Since no one is going to cut in to a pipe they can't shut off that prevents later plumbing work from leaving the home ungrounded.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- Make Your Bed: 9 DIY Headboards
- Insanely Easy 60-Minute Home Improvements
- 10 Cool Shipping Container Homes
- 9 Perfect Color Combos for Your Home
- 22 Tiny Houses We Love
- See the Most Highly Anticipated Colors for 2015
- Assembly Required: 15 DIY Kit Homes
- Favorite Space-Saving Double-Duty Furniture
- 10 Low-Cost DIY Home Security Solutions
- Redecorate Without Spending a Dime: 10 Ideas
- 10 Houseplants You Can Grow Anywhere
- 9 Amazing Mobile Home Makeovers
- 10 Doable Designs for a DIY Rug
- 9 Alternative Uses for Toothpaste
- Live Large in a (Very) Small Space
- 8 Cheap and Unique DIY Nightstands
- 15 Eye-Catching Options for Your Front Door
- Supersize Your Small Bath with 8 Pro Tips