240 V Outlet
A standard 15-amp 120 volt socket (NEMA 5-15) will have two vertical parallel slots like this (| |) and also have a third round hole for the ground.
The wider slot connects to the white neutral conductor (grounded conductor) and the narrow slot connects to the black live (or hot) conductor.
You must make sure to preserve polarity when replacing these.
A 15-amp 240 volt socket (NEMA 6-15) will have two slots in tandem like this: - - plus a third round hole for the equipment ground conductor.
The 20 amp version (NEMA 6-20) will have one vertical and one horizontal (| -).
The colors of these wires (in the ones I've opened) are usually black and red. The green is always supposed to be used for GROUND.
Now here is where it gets confusing: The 120 volt/20 amp socket (NEMA 5-20) looks like this: (- |) - a mirror image of the 240 volt 20-amp socket.
A 120 volt socket must NEVER be used on a 240 volt circuit for just that reason - CONFUSION by an end user.
You might want to test all the outlets in your house and have an electrician replace whatever looks bogus (if you don't know how to do it).
Joe, feel free to correct me.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- See the Most Highly Anticipated Colors for 2015
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 10 Unexpected Spots for Accent Colors
- 10 Fantastic Furniture Makeovers
- Worth It: 8 Renovations That Pay You Back
- 9 Closet Storage Tips from a Pro Organizer
- 7 Seriously Surprising Spots for a Fireplace
- Laundry Room Ideas to Knock Your Socks Off
- 12 Tiny Gardens to Grow on a Tabletop
- Supersize Your Small Bathroom with 8 Tips
- Kitchen Envy: 10 Rooms We Love