We recently purchased a two-story house with two heating zones (baseboard hot water). Unfortunately, it appears that the zones are wired together. No matter which thermostat kicks on, both circulating pumps come on, and we have heat coming on both floors. I did use a circuit tester to check, and yes, both pumps do come on together all the time. Each pump has its own box that controls it (where the thermostat wire comes in). I believe this is the source of the problem. Each box has six terminals, labeled 1-6. Can anyone tell me where these wires SHOULD go? The hot terminals that go to the pump are actually double-tapped, with a second wire heading to the furnace, which I think is the problem. Please help - thanks!
Each t-stat should go to it'sown pump relay. Line voltage the same, to each pump relay. Once the t-stat calls, only one box should come on and energize only 1 pump. Sounds like either the t-stats are possibly shorted in the wall and bringing on the pumps together or the pumps themselves are wired together. Where the lo voltage wire comes into the box, Disconnect and cross the terminals. You will be acting as the t-stat to make the pump relay come on.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 11 Lessons to Learn from AirBnB's Tiniest Homes
- 10 DIY Ways to Redo Your Wall—Without Paint
- 8 Smart Shoe Racks You Can Make Today
- 7 Easy Budget-Friendly Backyard Makeovers
- Worth It: 8 Renovations That Pay You Back
- 7 House Sounds Never to Ignore
- Watch These 10 Home Trends Take Off in 2015
- 11 Things Never to Keep in Your Bedroom
- 12 Places You Never Clean—But Should!