furnace won't fire
If the nipple isn't clogged, pull off the hose completely and check it for obstructions. Also poke the nipple at the sensor. If that doesn't work, pull the combustion air duct off the top of the unit and make sure it's drafting. You should feel air turbulance at the duct opening. If it's not drafting, you probably have a bird's nest or leaves stuck in there.
If it's not the air sensor, then it may be something serious like the control module. Run the furnace and let it shut down of it's own accord, open up the combustion chamber on the bottom and check the LED code. It will probably be blinking, or perhaps have an error code. Check this against the troubleshooting guide in you owner's manual.
The unit will not run with the combustion chamber open, so you will have to put the access panel back in place to see if its working.
- 15 Old House Features We Were Wrong to Abandon
- 17 Tiny Bathrooms We Love
- 20 Insanely Easy 60-Minute Home Improvements
- 17 Design Inspirations for Mudrooms and Entryways
- 25 Clever Ideas for Repurposed Storage
- 16 Inventive Beds You Can Make Yourself
- Laundry Room Ideas to Knock Your Socks Off
- 30 Things Every Homeowner Should Know How to Do
- 11 Clever Alternatives to Kitchen Cabinets
- 159 Storage Ideas for Space-Starved DIYers
- 21 "Expert Picks" for Fail-Safe Colors
- 9 Easy Ways to Kill Weeds Effectively
- 20 Ways to Make a Small Bathroom Big
- Simple “Under $60” Curb Appeal Updates for Any Home
- 67 Expert Tips to Aid Your Spring Cleaning
- 10 Eye-Catching Options for Your Front Door
- 10 Room Dividers to Bring Order to Your Space
- 11 Creative Garden Borders You Can Make—Easily!
- Tips and Tricks to Fit More into Less Closet Space
- Secret Rooms: 10 Special Spaces Hidden from Sight