You didn't say what kind of plumbing you've installed. If it's plastic, there's no point in placing a ground on it.
Is there a grounding rod outside?
[This message has been edited by rpxlpx (edited December 03, 2002).]
Yes, I have a grounding wire that is going outside. I am putting either PVC or copper plumbing back in.
Any copper plumbing you install should be bonded back to the bonded buss bar in the service or building disconnecting means. In order to serve as a grounding electrode for your home the clamp should be attached to an underground metal water pipe within five feet of were it enters your home. There must not be any plastic pipe or insulating fittings between the point of attachment and the underground piping. The best practice is to make the grounding connection on the supply side of the first control valve in the water line. Since no one is going to cut in to a pipe they can't shut off that prevents later plumbing work from leaving the home ungrounded.
- 10 Old House Features We Were Wrong to Abandon
- 11 Tiny Bathrooms We Love
- 12 Insanely Easy 60-Minute Home Improvements
- Kitchen Envy: 10 Rooms We Love
- 25 Clever Ideas for Repurposed Storage
- 10 Surprising Ways to Cure Household Odors
- 11 Ways to Winterize Your Home on a Budget
- 10 Ways to Live Large in a Small Space
- 10 Eye-Catching Options for Your Front Door
- Dressing Up the Dresser: 11 Clever DIY Transformations
- 12 Hobbit Houses to Make You Consider Moving Underground
- 10 Ways to Use Mirrors to Your Design Advantage
- 10 New Uses for Old Doors
- How To: Paint EVERYTHING
- Man, Oh Man! 7 Unbelievable Guy Spaces
- Assembly Required: 15 DIY Kit Homes
- 12 Wow-Worthy Woods for Kitchen Countertops
- 10 "Neat" Garage Storage Solutions
- 10 Houseplants to Improve Indoor Air Quality
- How To: Clean EVERYTHING