Replaced an old water heater with a new 40 gal. gas water heater. Used new water pipe port adaptors (3/4 npt to 3/4 copper)in the tank ports. After cleaning the threads I applied teflon tape to the threads and tightened the adaptors tight. After heating the water heater up to temperature (130 deg) I have a very, very small leak coming through the tank port threads (both hot and cold). What is my problem ?? I am a fairly experienced do it yourselfer.
Hello and welcome to the forums. Your problem is easy to fix. The adapters coming off the HWH are not tight enough. You will have to cut the pipes, retighten the adapters with a large adjustable wrench, and install (2) CxC slip couplings and resolder. Use PIPE DOPE on the male threads only. It's possible you miswrapped your teflon tape. When you use dope, you can't go wrong.
Water heater installation help.
hot water return line issue / valve tips?
Hydronic Heat, Indirect Water Heater, No Hot Water, ...
Water Heater Leak
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 8 Cleaning Mistakes Everyone Makes
- 10 Insanely Creative Shelves You Can DIY
- 10 Bargain Organizers for a Tidy Garage
- 7 Easy Budget-Friendly Backyard Makeovers
- 9 Backyard Fire Pits You Can Afford
- 10 Things You Didn't Know Windex Can Do
- Watch These 10 Home Trends Take Off in 2015
- Surprisingly Simple Woodworking Projects
- 16 Garden Borders You Can Make—Easily!