Replaced an old water heater with a new 40 gal. gas water heater. Used new water pipe port adaptors (3/4 npt to 3/4 copper)in the tank ports. After cleaning the threads I applied teflon tape to the threads and tightened the adaptors tight. After heating the water heater up to temperature (130 deg) I have a very, very small leak coming through the tank port threads (both hot and cold). What is my problem ?? I am a fairly experienced do it yourselfer.
Hello and welcome to the forums. Your problem is easy to fix. The adapters coming off the HWH are not tight enough. You will have to cut the pipes, retighten the adapters with a large adjustable wrench, and install (2) CxC slip couplings and resolder. Use PIPE DOPE on the male threads only. It's possible you miswrapped your teflon tape. When you use dope, you can't go wrong.
Water heater installation help.
hot water return line issue / valve tips?
Hydronic Heat, Indirect Water Heater, No Hot Water, ...
Water Heater Leak
- 15 Old House Features We Shouldn't Abandon
- 13 Lazy Cleaning Tricks for a Spotless Home
- Laundry Room Ideas to Knock Your Socks Off
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 7 House Sounds You Never Want to Ignore
- 10 Surprisingly Simple Woodworking Projects
- Worth It: 8 Renovations That Pay You Back
- Organize Your Life with 12 Dollar-Store Buys
- 9 Totally Amazing Mobile Home Makeovers
- Don't Make These 7 Mistakes in Small Spaces
- 20 Sneaky Storage Ideas
- 15 Totally Unexpected DIY Flooring Alternatives
- 7 Easy Budget-Friendly Backyard Makeovers
- 10 Closet Cures That Cost Less Than $100
- 11 Easy DIY Projects to Declutter Your Home
- 10 "Zero Dollar" Garden Hacks
- 10 Killproof Plants for a No-Effort Landscape
- 9 Insanely Easy 1-Hour Backyard Projects