I have read that you can add a Circuit breaker GFCI to your breaker box.
yes, most panel manufacture's have GFI breakers available
Does it make any sence to add a GFCI circuit breaker to the box if I already am protected with the GFCI outlets?
It will then protect the circuit itself, which the plain GFI receptacles cannot do
Would it conflict with the outlets that are allready installed? Will it provide more safety?
It will not conflict, however , there is the possiblity of 'nusaince tripping' here.
For instance, if you were to have one of the newer gas ranges receptacle ( for the ignitor) served via GFI it would trip it.
There are also dimmers, as well as other electrical devices that may conflict with the 4-6 ma trip rating of a GFI.
Perhaps you should inquire of your local tradesmen about the new AFCI , and get thier take on your situation .
The other type of protection device isnt made to protect the bathroom, it is to protect the circuit from bad devices, or errant drill or saw blades. Say you have a light that has a damaged cord, the breaker will protect against that. National code now requires every bedroom circuit be protected by an Arc Fault device and all bathrooms and outlets near water, such as a kitchen or laundry area be protected by GFCI.
Here is what the 2 devices do; The AFI is a UL listed circuit breaker which is also classified for mitigating the effects of arcing faults. It protects from arcs between current carrying conductors above 75A (Square D AFI protects from arcs above 50A), and leakage to ground above 30mA.
The GFI is a UL listed circuit breaker which is classified for interrupting the circuit when more than 6mA of ground-fault leakage is detected.
In other words, the arc fault device wont protect against water hazards like the GFCI will, but the GFCI is too sensitve to protect against frayed light cords.
[This message has been edited by electricmanscott (edited October 18, 2002).]
what would i tell a potential customer?
exactly what you allude to....
1)update the service
2)install new branch circuitry for those dedicated loads
3)lessen the lodas on any older circuitry, either via splitting up older circuits into 2-3 and/or derating those older 20A circuits to 15A
4)then, and only then, research options for said remaining older ciruitry.
One should not advocate AFCI's or GFCI's for the 'bandaid' approach......
- 15 Old House Features We Were Wrong to Abandon
- 17 Tiny Bathrooms We Love
- 20 Insanely Easy 60-Minute Home Improvements
- 70 Gardening Tricks and Ideas for Total Beginners
- 16 Inventive Beds You Can Make Yourself
- Top 10 Classic DIY Projects for the Outdoors
- 15 Once-Popular Household Items That Are Vanishing
- 159 Smart Storage Ideas for the Whole House
- 30 Things Every Adult Should Know How to Do
- 10 Wise Ways to Get Rid of Pests and Critters
- 9 Totally Amazing Mobile Home Makeovers
- Top Tips for Keeping Countertops Like New
- 15 Amazing Things You Can Make with $0 Scrap Wood
- 14 Ways to Get More Kitchen Counter Space
- Assembly Required: 15 DIY Kit Homes
- 18 Bathroom Updates You Can Do in 1 Day
- 9 Tried-and-True Methods of Eliminating Weeds
- Top 11 Color Trends to Follow in 2014
- 11 Clever Alternatives to Kitchen Cabinets
- 7 Easy Budget-Friendly Backyard Makeovers
- 10 Laundry Room Ideas to Knock Your Socks Off
- 10 “Stone Sober” Household Uses for Liquor
- 10 Fun Planters to Make with Everyday Objects
- 15 Spring Home Maintenance Musts
- 20 Ways to Make a Small Bathroom Big
- Man, Oh Man! 7 Unbelievable Guy Spaces
- 14 Room Dividers to Organize Your Space
- Wow-Worthy Window Films: 11 Top Picks
- 10 Houseplants to Improve Air Quality
- 10 Ingenious Home Uses for Baking Soda