We have an old apartment building. It is wired with two-prong outlets fed by two-wire cable (hot and neutral, no ground).
When I test these outlets using a pen-style tester (the kind that "senses" current without actually touching the wire) both side give a hot reading.
The outlets work fine otherwise (appliances plugged into them work).
When I test the outlets in my home (with grounded outlets) one side tests hot, the other doesn't.
What's happening with the older outlets? Is this a problem that needs to be fixed? If so, how? Hopefully not by rewiring the entire building.
You should be alright. Some tickers will show what you describe. Mine does on occasion. If I put mine next the neutral wire in some outlets, it will show live. I have never worried about it. You are fine.
- 10 Old House Features We Were Wrong to Abandon
- 11 Tiny Bathrooms We Love
- 12 Insanely Easy 60-Minute Home Improvements
- Kitchen Envy: 10 Rooms We Love
- 25 Clever Ideas for Repurposed Storage
- 10 Surprising Ways to Cure Household Odors
- 11 Ways to Winterize Your Home on a Budget
- 10 Ways to Live Large in a Small Space
- 10 Eye-Catching Options for Your Front Door
- Dressing Up the Dresser: 11 Clever DIY Transformations
- 12 Hobbit Houses to Make You Consider Moving Underground
- 10 Ways to Use Mirrors to Your Design Advantage
- 10 New Uses for Old Doors
- How To: Paint EVERYTHING
- Man, Oh Man! 7 Unbelievable Guy Spaces
- Assembly Required: 15 DIY Kit Homes
- 12 Wow-Worthy Woods for Kitchen Countertops
- 10 "Neat" Garage Storage Solutions
- 10 Houseplants to Improve Indoor Air Quality
- How To: Clean EVERYTHING