We have an old apartment building. It is wired with two-prong outlets fed by two-wire cable (hot and neutral, no ground).
When I test these outlets using a pen-style tester (the kind that "senses" current without actually touching the wire) both side give a hot reading.
The outlets work fine otherwise (appliances plugged into them work).
When I test the outlets in my home (with grounded outlets) one side tests hot, the other doesn't.
What's happening with the older outlets? Is this a problem that needs to be fixed? If so, how? Hopefully not by rewiring the entire building.
You should be alright. Some tickers will show what you describe. Mine does on occasion. If I put mine next the neutral wire in some outlets, it will show live. I have never worried about it. You are fine.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 11 Lessons to Learn from AirBnB's Tiniest Homes
- 10 DIY Ways to Redo Your Wall—Without Paint
- 8 Smart Shoe Racks You Can Make Today
- 7 Easy Budget-Friendly Backyard Makeovers
- Worth It: 8 Renovations That Pay You Back
- 7 House Sounds Never to Ignore
- Watch These 10 Home Trends Take Off in 2015
- 11 Things Never to Keep in Your Bedroom
- 12 Places You Never Clean—But Should!