We have an old apartment building. It is wired with two-prong outlets fed by two-wire cable (hot and neutral, no ground).
When I test these outlets using a pen-style tester (the kind that "senses" current without actually touching the wire) both side give a hot reading.
The outlets work fine otherwise (appliances plugged into them work).
When I test the outlets in my home (with grounded outlets) one side tests hot, the other doesn't.
What's happening with the older outlets? Is this a problem that needs to be fixed? If so, how? Hopefully not by rewiring the entire building.
You should be alright. Some tickers will show what you describe. Mine does on occasion. If I put mine next the neutral wire in some outlets, it will show live. I have never worried about it. You are fine.
- 15 Old House Features We Shouldn't Abandon
- 13 Lazy Cleaning Tricks for a Spotless Home
- Laundry Room Ideas to Knock Your Socks Off
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 7 House Sounds You Never Want to Ignore
- 10 Surprisingly Simple Woodworking Projects
- Worth It: 8 Renovations That Pay You Back
- Organize Your Life with 12 Dollar-Store Buys
- 9 Totally Amazing Mobile Home Makeovers
- Don't Make These 7 Mistakes in Small Spaces
- 20 Sneaky Storage Ideas
- 15 Totally Unexpected DIY Flooring Alternatives
- 7 Easy Budget-Friendly Backyard Makeovers
- 10 Closet Cures That Cost Less Than $100
- 11 Easy DIY Projects to Declutter Your Home
- 10 "Zero Dollar" Garden Hacks
- 10 Killproof Plants for a No-Effort Landscape
- 9 Insanely Easy 1-Hour Backyard Projects