I attended a home inspection of a place I am considering purchasing. The electrical issues are giving me some concern. The inspector showed me his concerns with the main and subpanel. Apparently, a subpanel was installed at some point. The current owner double lugged the main lugs (after the 200A breaker in the main panel) for the subpanel. He used a 'main only' subpanel with no disconnects in the subpanel. Many branch circuits are used in the subpanel. The subpanel and main panels are right next to each other. Does this sound like the subpanel addition was properly done given that he used the 200A breaker in the main panel for a disconnect? I thought that you needed a disconnect in the subpanel as well. Does the location of the subpanel discount the use of a subpanel breaker or disconnect? Also, There are several brach circuit breakers that are double lugged. I understand that this is not up to NEC, correct? Thanks!!
The install of the subpanel was not installed properly and the inspector was right in expressing concern. The feeder overcurrent protection device cannot exceed the rating of the panelboard. The subpanel should have been protected by it's own overcurrent protection device. Double lugging is wrong and goes against the code.
U.S.M.C. Semper Fi !!!
U.S.M.C. Semper Fi !!!
The home inspector may or may not be correct. There are lugs and breakers that are listed and approved for more than a single conductor. If the wire was rated for 200 amps feeding the sub and was indeed after the 200 amp main it is perfectly legal to install without an additional disconnecting means. Your best bet if you have these concerns is to call a qualified licensed electrical professional to assess the installation. Most home inspecors I have personally been involved with are very limited in thier mechanical trades background and sometimes interpret codes or other information incorrectly.
Installing a subpanel in the basement
Relocating the electrical subpanel
100 amp lub subpanel from 200 amp main service panel
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 30 Things Everyone Should Know
- 25 Insanely Easy-to-Make Holiday Ornaments
- 20 Easy 60-Minute Home Improvements
- 10 Classic Ways to Brighten Up a Dark Room
- 10 Quick and Creative Stocking Stuffers
- 133 Smart Storage Ideas for the Whole House
- 7 Unauthorized Uses for Common Appliances
- 8 Ways to Make a Small Room Look Big
- Best Secret Hiding Spots We've Ever Seen
- Sweet Dreams: 15 Inventive Beds You Can Make Yourself
- 11 Ways to Winterize Your Home
- Laundry Room Ideas to Knock Your Socks Off
- 10 Must-Do Projects for November
- 8 Cheap and Unique DIY Nightstands
- 15 Eye-Catching Options for Your Front Door
- Supersize Your Small Bath with 8 Pro Tips
- 8 Unique Ways to Build Your Own Table
- Woodworking for Beginners: 10 Projects
- 10 Houseplants You Can Grow ANYWHERE
- 10 Doable Designs for a DIY Rug
- 7 Incredible Uses for Salvaged Lumber
- 10 Bookcases You Can Make Yourself
- 7 Mistakes Not to Make with Your Fireplace
- The Easy 1-Hour Money-Saving Home Checkup
- Quick Fixes for a Fresher Shower
- Don't Try This at Home: 7 Dangerous DIYs
- 10 Ways to Redecorate Without Spending a Dime
- The Top 10 Artificial Christmas Trees