I have looked high and low for help on my simple 3 way switch. I know it's possible because all I did was move each switch 6 inches into a new box and forgot to label them. Everything worked prior to my disconnecting everything. I should mention that this is an older home (1955) and maybe they just don't do things the same now.
Switch #1 has the hot and neutral power coming into it, the 14/2 wire going to the light, and another strand of 14/2 going to switch #2. In box #2 I have both wires of that second strand of 14/2 and one more that I traced to the light as the neutral wire. So in total I am dealing with 6 wires in box #1 and 3 in box #2. Please tell me which ones go to the common and which go to the traveler poles.
Thanks a million to whomever knows the answer to this puzzle.
Get Help from Bob Vila
- Give-Aways & Offers
- Monthly Must Do's
- DIY Project Ideas
- Step-by-Step Guides
- Inspirational Photo Galleries