The question I have is this: I have remodeled our main floor bathroom. It was not ground faulted. At the main panel, the current breaker's neutral wire is too short to stretch from the neutral bar to the GFI. Is it Okay to splice in a "jumper" wire to complete the circuit?
Does a bathroom GFCI need to be 20A?
Get Help from Bob Vila
- Give-Aways & Offers
- Monthly Must Do's
- DIY Project Ideas
- Step-by-Step Guides
- Inspirational Photo Galleries