i'm a maintanence guy for my mom's apartment complex and needed help with the heater.
the tenant had no thermostat so i told him to just touch the R and W wires together to make the heat turn on...now he says the heat no longer goes on and i installed a new thermostat and the heater still doesn't go on but the pilot is still lit up and i'm pretty sure i hear gas flowing through but not sure...please help....
i tested the R and W wires on my multimeter and i get no juice flowing through them...does that mean the little motor is out or the wires are fried?
Because its a wall furnace and ones face has to be near the burners to do any testing near the main valve I shall decline to offer advice. But the voltage you read at the r& W terminal should probably be read on the MILIVOLT scale, a regular a/c voltage scale wont read it! look for your Milivolt scale.
- 10 Old House Features We Were Wrong to Abandon
- 11 Tiny Bathrooms We Love
- 12 Insanely Easy 60-Minute Home Improvements
- Kitchen Envy: 10 Rooms We Love
- 25 Clever Ideas for Repurposed Storage
- 10 Surprising Ways to Cure Household Odors
- 11 Ways to Winterize Your Home on a Budget
- 10 Ways to Live Large in a Small Space
- 10 Eye-Catching Options for Your Front Door
- Dressing Up the Dresser: 11 Clever DIY Transformations
- 12 Hobbit Houses to Make You Consider Moving Underground
- 10 Ways to Use Mirrors to Your Design Advantage
- 10 New Uses for Old Doors
- How To: Paint EVERYTHING
- Man, Oh Man! 7 Unbelievable Guy Spaces
- Assembly Required: 15 DIY Kit Homes
- 12 Wow-Worthy Woods for Kitchen Countertops
- 10 "Neat" Garage Storage Solutions
- 10 Houseplants to Improve Indoor Air Quality
- How To: Clean EVERYTHING