I've added a circuit for an electric dryer in my basement. The 4-post receptacle I installed is about six feet from the breaker box, connected by 10-gauge stranded wire (two hot, one neutral, and a ground) through flexible conduit.
The dryer started, but tripped the breaker after running several minutes. I reset the breaker and again after several minutes it tripped.
I was convinced that there was a short somewhere in my wiring until I looked at the instruction book and saw a picture of the breaker ...
I'd installed a double-pole GE breaker for this 30 amp circuit. It had "15A" written beside each switch (15 + 15 + 30 amps, right?)
But, the picture in my wiring book is of someone holding a double pole breaker with "30" written on each switch.
Did I install a breaker for only half the required amperage? The 10-gauge red & black wires should EACH be able to carry 30 amps, right?
I'm just afraid of putting-in a breaker that's too big and starting a fire if there really is a short somewhere.
- 15 Old House Features We Shouldn't Abandon
- 13 Lazy Cleaning Tricks for a Spotless Home
- Laundry Room Ideas to Knock Your Socks Off
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 7 House Sounds You Never Want to Ignore
- 10 Surprisingly Simple Woodworking Projects
- Worth It: 8 Renovations That Pay You Back
- Organize Your Life with 12 Dollar-Store Buys
- 9 Totally Amazing Mobile Home Makeovers
- Don't Make These 7 Mistakes in Small Spaces
- 16 Sneaky Storage Ideas
- 15 Totally Unexpected DIY Flooring Alternatives
- 7 Easy Budget-Friendly Backyard Makeovers
- 10 Closet Cures That Cost Less Than $100
- 11 Easy DIY Projects to Declutter Your Home
- 10 "Zero Dollar" Garden Hacks
- 10 Killproof Plants for a No-Effort Landscape
- 9 Insanely Easy 1-Hour Backyard Projects