I've added a circuit for an electric dryer in my basement. The 4-post receptacle I installed is about six feet from the breaker box, connected by 10-gauge stranded wire (two hot, one neutral, and a ground) through flexible conduit.
The dryer started, but tripped the breaker after running several minutes. I reset the breaker and again after several minutes it tripped.
I was convinced that there was a short somewhere in my wiring until I looked at the instruction book and saw a picture of the breaker ...
I'd installed a double-pole GE breaker for this 30 amp circuit. It had "15A" written beside each switch (15 + 15 + 30 amps, right?)
But, the picture in my wiring book is of someone holding a double pole breaker with "30" written on each switch.
Did I install a breaker for only half the required amperage? The 10-gauge red & black wires should EACH be able to carry 30 amps, right?
I'm just afraid of putting-in a breaker that's too big and starting a fire if there really is a short somewhere.
- 15 Old House Features We Were Wrong to Abandon
- 17 Tiny Bathrooms We Love
- 20 Insanely Easy 60-Minute Home Improvements
- 70 Gardening Tricks and Ideas for Total Beginners
- 16 Inventive Beds You Can Make Yourself
- 142 Remarkable Houses Around the World
- 11 Clever Alternatives to Kitchen Cabinets
- 7 Easy Budget-Friendly Backyard Makeovers
- 159 Smart Storage Ideas for the Whole House
- 10 Room Dividers to Bring Order to Your Space
- Shelf Life: 10 Bookcase Projects You Can DIY
- 11 Creative Garden Borders You Can Make—Easily!
- Tips and Tricks to Fit More into Less Closet Space
- 11 Amazing Homemade Sheds to Inspire Your Own
- Secret Rooms: 10 Special Spaces Hidden from Sight
- 17 Design Inspirations for Mudrooms and Entryways
- Recipe for Success: 10 Easy Kitchen Storage Hacks
- Winning Combinations: 9 "Can't Miss" Color Schemes
- Laundry Room Ideas to Knock Your Socks Off
- The Ultimate All-Natural Cleaning Guide