I've added a circuit for an electric dryer in my basement. The 4-post receptacle I installed is about six feet from the breaker box, connected by 10-gauge stranded wire (two hot, one neutral, and a ground) through flexible conduit.
The dryer started, but tripped the breaker after running several minutes. I reset the breaker and again after several minutes it tripped.
I was convinced that there was a short somewhere in my wiring until I looked at the instruction book and saw a picture of the breaker ...
I'd installed a double-pole GE breaker for this 30 amp circuit. It had "15A" written beside each switch (15 + 15 + 30 amps, right?)
But, the picture in my wiring book is of someone holding a double pole breaker with "30" written on each switch.
Did I install a breaker for only half the required amperage? The 10-gauge red & black wires should EACH be able to carry 30 amps, right?
I'm just afraid of putting-in a breaker that's too big and starting a fire if there really is a short somewhere.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 21 Ways to Spring Clean—Naturally
- Show Off: 9 Ways to Display a Collection
- The Best Paint Colors for Low-Light Rooms
- 7 Easy Budget-Friendly Backyard Makeovers
- 8 Clever Storage Solutions for Pots & Pans
- 8 Creative OTHER Ways to Use a Closet
- 12 Tiny Gardens to Grow on a Tabletop
- 15 Eye-Catching Front Door Options
- 12 Places You Never Clean—But Should!