I've added a circuit for an electric dryer in my basement. The 4-post receptacle I installed is about six feet from the breaker box, connected by 10-gauge stranded wire (two hot, one neutral, and a ground) through flexible conduit.
The dryer started, but tripped the breaker after running several minutes. I reset the breaker and again after several minutes it tripped.
I was convinced that there was a short somewhere in my wiring until I looked at the instruction book and saw a picture of the breaker ...
I'd installed a double-pole GE breaker for this 30 amp circuit. It had "15A" written beside each switch (15 + 15 + 30 amps, right?)
But, the picture in my wiring book is of someone holding a double pole breaker with "30" written on each switch.
Did I install a breaker for only half the required amperage? The 10-gauge red & black wires should EACH be able to carry 30 amps, right?
I'm just afraid of putting-in a breaker that's too big and starting a fire if there really is a short somewhere.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 11 Signs of an Unhappy Houseplant
- Insanely Easy 60-Minute Home Improvements
- 10 Cool Shipping Container Homes
- 9 Perfect Color Combos for Your Home
- 22 Tiny Houses We Love
- See the Most Highly Anticipated Colors for 2015
- Assembly Required: 15 DIY Kit Homes
- Favorite Space-Saving Double-Duty Furniture
- 10 IKEA Favorites, DIY Style
- Redecorate Without Spending a Dime: 10 Ideas
- 10 Houseplants You Can Grow Anywhere
- 9 Amazing Mobile Home Makeovers
- 10 Doable Designs for a DIY Rug
- 9 Alternative Uses for Toothpaste
- Live Large in a (Very) Small Space
- 8 Cheap and Unique DIY Nightstands
- 15 Eye-Catching Options for Your Front Door
- Supersize Your Small Bath with 8 Pro Tips