I am trying to install an in wall timer switch for my exterior lights. The timer does require a white nuetral wire. My house is brand new, and I know it should have a white nuetral wire. There is what looks like 3 white wires joined by a nut but not connected to any switch, is this the nuetral? The switch I am trying to replace is a single switch. It has two red wires connected to 1 of the screws and two orange wires connected to the other screw. I am not sure which one is the 'hot' and which is the 'load' as they do not match the colors I am used to. There is also no visible copper ground wire or green screw. I am not sure what steps to take next. Timer has 3 wires needing to be connected. A black to go to a hot wire, a red to go to the load wire, and a green to go to ground wire. Any help would be appreciated.
"There is what looks like 3 white wires joined by a nut but not connected to any switch, is this the nuetral?" More than likely the three bundle is the neutral. The line would be the one that is hot all the time and the load would be the one that is hot when the switch is on and cold when the switch is in the off position. Also are you sure two wires connect to one screw? Not code. Maybe it's just stranded wire around the screw with insulation left on to prevent unraveling.
So after looking at it, it is not two wires, but one with the wire exposed and wrapped around the screw before heading elsewhere. One end of each red wire goes into the wall and then after wrapping around the screw the other end connects with the other switch. The switch on the left of the picture is to the interior ceiling light (I do not want to change anything with that one, the switch on the right controls 3 coach lights on the exterior(this is the one I am putting a timer on). If the white bundle on the bottom of picture is the nuetral, then I am still not sure where to connect my green ground wire. Besides putting up a ceiling fan, I do not know much about electrical. Any help is appreciated.
I was able to install the timer by experimenting. I connected the nuetral wire to the white bundle on the bottom, the black hot wire to the red wire from the current switch (since it was the only color going to both original switches, I figured it had to be the hot), The load wire to the orange and connected the green wire to the green 'ground' screw on the other original light switch. It is working great.
Multiple Lights In a Single Switch
Combining 2 switches into 1?
In-Wall 120V Timers
how to install GFCI protection on multiwire branch c...
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 30 Things Everyone Should Know
- 25 Insanely Easy-to-Make Holiday Ornaments
- 20 Easy 60-Minute Home Improvements
- 10 Classic Ways to Brighten Up a Dark Room
- 10 Houseplants to Improve Indoor Air Quality
- 133 Smart Storage Ideas for the Whole House
- 7 Unauthorized Uses for Common Appliances
- 8 Ways to Make a Small Room Look Big
- Best Secret Hiding Spots We've Ever Seen
- Sweet Dreams: 15 Inventive Beds You Can Make Yourself
- 11 Ways to Winterize Your Home
- Laundry Room Ideas to Knock Your Socks Off
- 17 Creative Ways to Repurpose Cardboard
- 8 Cheap and Unique DIY Nightstands
- 15 Eye-Catching Options for Your Front Door
- Supersize Your Small Bath with 8 Pro Tips
- 8 Unique Ways to Build Your Own Table
- Woodworking for Beginners: 10 Projects
- 10 Houseplants You Can Grow ANYWHERE
- 10 Doable Designs for a DIY Rug
- 7 Incredible Uses for Salvaged Lumber
- 10 Bookcases You Can Make Yourself
- 7 Mistakes Not to Make with Your Fireplace
- The Easy 1-Hour Money-Saving Home Checkup
- Quick Fixes for a Fresher Shower
- Don't Try This at Home: 7 Dangerous DIYs
- 10 Ways to Redecorate Without Spending a Dime
- 16 Coffee Tables You Can DIY—Easily!