1. Breaker: Easy to check, probably not the cause, switch it with another breaker of the same amperage.
2. Short: Probably not the cause either since it only does it occasionally, unless, when the water reaches a certain level it bridges the gap and causes the short.
3. Overamp: Most likely cause- two possibilities:
A. Pump is partially jammed or binding from old age. Since the pump is not turning freely it is putting a strain on the motor causing it to overwork and heat up. When this happens the motor begins to exceed the amperage rating causing the breaker to trip.
B. Motor itself. As motors age the internal parts break down causing problems. Either the windings become shorted, the bearings begin to seize (similar to the pump problem), etc. For whatever reason the motor will itself overamp and trip the breaker.
The overamping can be verified with an amprobe without going into the well.
Notice the diagramming, paid attention in school. I am not certain what your control box does, but I really cannot see it or the pressure switch causing a tripping problem unless it shorts out from the water. But all of these are usually under water constantly unless yours is a remote setup.
If I missed anything?????
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 11 Lessons to Learn from AirBnB's Tiniest Homes
- 10 DIY Ways to Redo Your Wall—Without Paint
- 8 Smart Shoe Racks You Can Make Today
- 7 Easy Budget-Friendly Backyard Makeovers
- Worth It: 8 Renovations That Pay You Back
- 7 House Sounds Never to Ignore
- Watch These 10 Home Trends Take Off in 2015
- 11 Things Never to Keep in Your Bedroom
- 12 Places You Never Clean—But Should!