1. Breaker: Easy to check, probably not the cause, switch it with another breaker of the same amperage.
2. Short: Probably not the cause either since it only does it occasionally, unless, when the water reaches a certain level it bridges the gap and causes the short.
3. Overamp: Most likely cause- two possibilities:
A. Pump is partially jammed or binding from old age. Since the pump is not turning freely it is putting a strain on the motor causing it to overwork and heat up. When this happens the motor begins to exceed the amperage rating causing the breaker to trip.
B. Motor itself. As motors age the internal parts break down causing problems. Either the windings become shorted, the bearings begin to seize (similar to the pump problem), etc. For whatever reason the motor will itself overamp and trip the breaker.
The overamping can be verified with an amprobe without going into the well.
Notice the diagramming, paid attention in school. I am not certain what your control box does, but I really cannot see it or the pressure switch causing a tripping problem unless it shorts out from the water. But all of these are usually under water constantly unless yours is a remote setup.
If I missed anything?????
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 8 Smart Shoe Racks You Can Make Today
- Insanely Easy 60-Minute Home Improvements
- 30 Things Every Adult Should Know How to Do
- 9 Things You Never Thought to Paint—But Should
- 12 Sheds You Could Live (or Work) In
- 16 Designs for a Low-Cost DIY Coffee Table
- Assembly Required: 15 DIY Kit Homes
- 10 Surprisingly Simple Woodworking Projects
- 9 Totally Amazing Mobile Home Makeovers
- Storage Where You Least Expected It
- 9 Best Lighting Picks for Your Bedroom
- 22 Tiny Houses We Love
- 9 Closet Storage Tips from a Pro Organizer
- See the Most Highly Anticipated Colors for 2015
- Laundry Room Ideas to Knock Your Socks Off
- 12 Tiny Gardens to Grow on a Tabletop
- Supersize Your Small Bathroom with 8 Tips
- 10 Alternatives to a Traditional Home Office