I am finishing an attic above a garage for another bedroom. There is an HVAC unit upstairs for the bedroom and media room already there. I would like to vent this new room with this unit. It is right next to the new room. How do you and where do you cut into the current ducts to add the addional vent? Is there is website that gives pictures or explanations on how to do this. I am assuming it is not very difficult.
You cut into the supply trunk for additional "hits". Assumming you have the room / access, purchase a 6" starter collar, and trace out the circle on the supply duct. When you have the circle cut out, you simply bend the tabs back on the collar, and they hold it in place. Then you can install 6" ridgid circular pipe, or for easier installation in tight spaces use insulated flex pipe. The flex pipe is more expensive, but saves time and requires virtually no fittings.
Along with the start collar, you will need a register 'boot' if you are using floor registers. These to can be purchased at home centers. If you cannot hard pipe to the floor boot. As a last resort I would use flex. It is insulated but the airflow lose incountered with this is stagering.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 8 Cleaning Mistakes Everyone Makes
- 10 Insanely Creative Shelves You Can DIY
- 10 Bargain Organizers for a Tidy Garage
- 7 Easy Budget-Friendly Backyard Makeovers
- 9 Backyard Fire Pits You Can Afford
- 10 Things You Didn't Know Windex Can Do
- Watch These 10 Home Trends Take Off in 2015
- Surprisingly Simple Woodworking Projects
- 16 Garden Borders You Can Make—Easily!