I say a 100' because I have to run from the whole length of the house then out the side and back to where the shed is.
If you want outside lights at both the house and the shed that you can control from either end then you will want four wires plus ground and it may be hard to find UF cable in ten gauge with four insulated conductors. In that case you can bury a PVC conduit under one foot of earth if you protect the circuit with a GFCI. If you bury the conduit under eighteen inches of earth you will not have to provide GFCI protection and you can avoid any possibility of nuisance tripping of the circuit do to moisture in the underground conduit or cable. You would also need to make sure that the conductors serving the outside light never enter the interior of the shed or that there is a switch that will deenergize the entire circuit were it originates in the house.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 11 Lessons to Learn from AirBnB's Tiniest Homes
- 10 DIY Ways to Redo Your Wall—Without Paint
- 8 Smart Shoe Racks You Can Make Today
- 7 Easy Budget-Friendly Backyard Makeovers
- Worth It: 8 Renovations That Pay You Back
- 7 House Sounds Never to Ignore
- Watch These 10 Home Trends Take Off in 2015
- 11 Things Never to Keep in Your Bedroom
- 12 Places You Never Clean—But Should!