electrical grounding for garage
Make sure that there are no other conductive paths between your garage & house, otherwise you need to add an equipment grounding conductor from the hous to the garage and treat the panel in the garage like a sub-panel by keeping the neutral & grounds separated. You'll still need 2 ground rods at the garage.
[This message has been edited by Tom O (edited October 15, 2002).]
The first, you state that the inside panel is grounded to the water line. Sadly, this location is not the service, which is where the grounding is required.
The second, you state you want to tie the wires for the garage into the outside box, below the meter. You can only do this using approved connections. You cannot install two wires under one screw (unless approved), so additional work will be required to tie in your conductors at this location.
You really should get help with this. There are alot of variables involved, and omitting any one could spell disaster for you or your loved ones.
- 15 Old House Features We Shouldn't Abandon
- 13 Lazy Cleaning Tricks for a Spotless Home
- Laundry Room Ideas to Knock Your Socks Off
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 7 House Sounds You Never Want to Ignore
- 10 Surprisingly Simple Woodworking Projects
- Worth It: 8 Renovations That Pay You Back
- Organize Your Life with 12 Dollar-Store Buys
- 9 Totally Amazing Mobile Home Makeovers
- Don't Make These 7 Mistakes in Small Spaces
- 20 Sneaky Storage Ideas
- 15 Totally Unexpected DIY Flooring Alternatives
- 7 Easy Budget-Friendly Backyard Makeovers
- 10 Closet Cures That Cost Less Than $100
- 11 Easy DIY Projects to Declutter Your Home
- 10 "Zero Dollar" Garden Hacks
- 10 Killproof Plants for a No-Effort Landscape
- 9 Insanely Easy 1-Hour Backyard Projects