electrical grounding for garage
Make sure that there are no other conductive paths between your garage & house, otherwise you need to add an equipment grounding conductor from the hous to the garage and treat the panel in the garage like a sub-panel by keeping the neutral & grounds separated. You'll still need 2 ground rods at the garage.
[This message has been edited by Tom O (edited October 15, 2002).]
The first, you state that the inside panel is grounded to the water line. Sadly, this location is not the service, which is where the grounding is required.
The second, you state you want to tie the wires for the garage into the outside box, below the meter. You can only do this using approved connections. You cannot install two wires under one screw (unless approved), so additional work will be required to tie in your conductors at this location.
You really should get help with this. There are alot of variables involved, and omitting any one could spell disaster for you or your loved ones.
- 15 Old House Features We Were Wrong to Abandon
- 17 Tiny Bathrooms We Love
- 20 Insanely Easy 60-Minute Home Improvements
- 17 Design Inspirations for Mudrooms and Entryways
- 25 Clever Ideas for Repurposed Storage
- 16 Inventive Beds You Can Make Yourself
- Laundry Room Ideas to Knock Your Socks Off
- 30 Things Every Homeowner Should Know How to Do
- 11 Clever Alternatives to Kitchen Cabinets
- 10 Planters You Can Make Out of Everyday Things
- 21 "Expert Picks" for Fail-Safe Colors
- Garden Paths: 12 Easy-to-Imitate Stone Walkways
- 20 Ways to Make a Small Bathroom Big
- 9 Incredible Faux Finishes Possible with Paint
- 10 Sly Spots Where You Can Stash Your Storage Stuff
- 10 Eye-Catching Options for Your Front Door
- 10 Room Dividers to Bring Order to Your Space
- 11 Creative Garden Borders You Can Make—Easily!
- Tips and Tricks to Fit More into Less Closet Space
- Secret Rooms: 10 Special Spaces Hidden from Sight