According to all the diagrams, I have wirwed my switches correctly, but the breaker continues to trip. Question is this...
from the breaker box, (with 14/2), the hot is pigtailed to go to 3 switches, with the resulting ends to the common screws of the switches. Red & black are on the travelers...then lead to the next set of switches. Does it matter WHICH traveler screws or are they interchangeable?
Also, AFTER the 2nd set of switches, I've got 14/2 going to the fixtures. The black from these is on the common as well....is this correct?
Thanks for a response!!!!
Get Help from Bob Vila
- Give-Aways & Offers
- Monthly Must Do's
- DIY Project Ideas
- Step-by-Step Guides
- Inspirational Photo Galleries